1 Watt 5.8Gz C Band Motion Activated Wall Switch Zero - Cross Point Operation
|Place of Origin||Shenzhen, China|
|Certification||RED, FCC, RoHS, ETL|
|Minimum Order Quantity||400pcs|
|Packaging Details||Bubble bag + carton. (color box or blister package also available on request)|
|Delivery Time||4 weeks for bulk orders|
|Supply Ability||50,000pcs / month|
|Function||Tri-level Dimming, Daylight Monitoring||Stand-by Power||<1w|
|Output Signal||1-10V Dimming Signal||Size||102*45*27.5mm|
|Setting||DIP Switch||IP Rating||IP20|
motion activated wall switch,
ac sensor switch
AC input , Dimmable microwace motion sensor , with daylight monitoring
Zero-cross point operation, protect the sensor relay against the in-rush current, secure the max. load and life time of the relay.
Dual-processor technology, real daylight monitoring function for built-in application.
|Input voltage:||120〜277V AC, 50/60Hz.|
800W @ 200〜277VAC (capacitive)
|Detection range:||up to 12m in diameter|
|Operation temperature:||-20℃~ +70℃|
Detection range: 100%, 75%, 50%, 25% for your options
Hold-time means the time period to keep the lamp on 100% after motion detected.
T3s, 30s,90s,5min,10min,30min for your options
Daylight sensor means the daylight threshold to enable or disable the sensor function.
"Disable": The sensor works always, even during daylight.
"50lux": The sensor works only in twilight.
"10lux, 2lux": The sensor works only in the dark.
This is the time period that the lamp remains at a low light level before it is completely switched off in the long absence of people.
“+∞”: means bi-level dimming control, the fixture never switch off.
10s,5min,10min,30min,1H, +∞ for your options
Stand-by dimming level
This is the dimmed low light level you would like to have after the hold-time in the absence of people.
*0% means on/off control.
10%--Vdim=1.5Vdc 30%--Vdim=3.0Vdc 50%--Vdim=5.0Vdc
0%, 10%, 30%, 50% for your options
Daylight monitoring function--
Utilizing the Dual-processor technology, this sensor can tell the difference of natural light and artificial light(lamp) from behind the diffuser, switch on automatically(even without movements) when the ambient light is below target value, and then switch off automatically whenever the artificial light is not required(ambient light is bright enough).
Note: Lux-Off sampling time---30s; Lux-On sampling time---10s.
Lux-On function takes effect only when standby dimming period set at+∞.