Microwave Motion Sensor Switch
Microwave Motion Sensor Module
Zhaga Book 18
Bluetooth Motion Sensor
Daylight Sensor Switch
12V Microwave Sensor
AC Motion Sensor Switch
High Bay Motion Sensor
Dimmable Motion Sensor
DALI Motion Sensor
Daylight Harvesting Sensor
High Frequency Motion Sensor
Presence Motion Detector
ETL Motion Sensor
Security Motion Sensor
LED Mirror Sensor
Advertising Display Sensor
Remote Controllable 12V Microwave Sensor , 12V Motion Detector
|Place of Origin||Shenzhen, China|
|Certification||RED, FCC, RoHS|
|Minimum Order Quantity||300pcs|
|Price||To be negotiated|
|Packaging Details||Bubble bag + carton. (color box or blister package also available on request)|
|Delivery Time||3~4 weeks for bulk orders|
|Supply Ability||50,000pcs / month|
Contact me for free samples and coupons.
Wechat: 0086 18588475571
If you have any concern, we provide 24-hour online help.x
|Input Voltage||12V DC (5V & 24V Version Available On Request)||Input Current||≥25mA|
|Control Type||Tri-level Dimming Control||Detection Range||Max. 12m In Diameter|
|Mounting Height||3~6m||Operation Temperature||-20℃ ~ +70℃|
12v motion detector,
12v motion sensor switch,
Remote Controllable 12V Microwave Sensor
1 ~ 10V Dimming Control , 12V Microwave Sensor , Remote Controllable , For Tri - Proof Fixture
12V DC input motion sensor with 1~10v dimming output, special housing designed for Tri-proof fixture application. Infrared remote for end-user to change all the settings. Dual-processor technology to differentiate the natural light and lamp light, daylight monitoring function available.
5.8GHz C-band microwave, tri-level dimming control.
Input voltage 12V DC (5V & 24V DC version available on request).
1~10V dimming output signal.
Super compact, flexible to be integrated into any suitable fixtures.
Dual-processor technology, real Daylight monitoring function for built-in application.
IR remote commissioning, easy setting and user friendly.
Detection range up to 12m in diameter.
Mounting height: 3~6m.
Operation temperature: -20°C~ +70°C.
Settings(by remote control IR12)--
Permanent ON/OFF function
Press “ON/OFF” button, fixture goes to permanent on or permanent off mode, sensor is disabled.
*press "Auto” ,”Reset" or “Ambient learn” to quit this mode.
Press "Dim" button to automatically dim up or down the light brightness during hold-time from 10% to 100%. Another press to lock it down when desired brightness is achieved.
*after desired brightness is locked down, if user wants to dim again reversely, just press the “Dim” button again and then lock down the new brightness again.
Press “Auto” button, the sensor starts to work and all settings remain the same as the latest status before the light was switched on/off.
Press”Reset” button, all settings go back to factory default settings.
*Factory default settings--
Press "Ambient learn" button, the latest surrounding lux value overwrites previous lux value learned, and set as the daylight threshold. This feature enables the fixture to function well in any real application circumstance.
"Test mode"is for testing purpose only, for users to check the functionality and choose the desired detection range. The sensor goes to test mode automatically after pressing this button.
Users can quit this mode by pressing "ON/OFF", "Reset' or any button of "Hold time". The sensor settings are changed accordingly.
*Test mode defaulted settings—
In this mode, when used for on/off control, after motion detected, sensor enters into a cycle of 3s on and 2s off. In this mode, when used for tri-level dimming control, after motion detected, sensor enters into a cycle of 3s on and 2s off(0.5s soft off + 1.5s off).
Daylight monitoring function--
Utilizing the Dual-processor technology, this sensor can tell the difference of natural light and artificial light(lamp) from behind the diffuser, switch on automatically(even without movements) when the ambient light is below target value, and then switch off automatically whenever the artificial light is not required (ambient light is bright enough).
This is the REAL& INTELLIGENT daylight monitoring sensor for built-in installation.
Note: Lux-Off sampling time—30s; Lux-On sampling time—10s.
Lux-On function takes effect only when standby dimming period set at +∞.