HNS204 AC Motion Sensor Switch IP20 Rating Detached Antenna Head
|Place of Origin||Shenzhen, China|
|Certification||CE, RED, FCC, RoHS|
|Minimum Order Quantity||300pcs|
|Price||To be negotiated|
|Packaging Details||Bubble bag + carton. (color box or blister package also available on request)|
|Delivery Time||3~4 weeks for bulk orders|
|Supply Ability||20,000pcs / month|
Contact me for free samples and coupons.
Wechat: 0086 18588475571
If you have any concern, we provide 24-hour online help.x
|Input Voltage||220~240V AC||Rated Load||400W(capacitive)|
|Stand-by Power||＜0.5W||Control Type||On/off Control|
|Detection Range||Max. 12m In Diameter||Mounting Height||3~6m|
|Operation Temperature||-20℃ ~ +70℃||IP Rating||IP20|
motion activated wall switch,
ac sensor switch,
AC Motion Sensor Switch IP20 Rating
On / Off Control , AC Motion Sensor Switch , Detached Antenna Head
Used together with ordinary non-dimmable LED driver, simple on/off control. Detached antenna head, ideal option for fixtures who have very limited space to mount the whole sensor body onto the LED plate.
End user can change setting by both DIP switch and remote control IR12.
5.8GHz C-band microwave motion sensor, on/off control.
Input voltage: 220~240V AC, 50Hz.
Rated load: 400W (capacitive)
Stand-by power: <0.5w.
Particularly designed for fixtures which with limited space, ideal for LED panels, linear office lights with metal louvres, compact bulkheads, etc. Hide the sensor body and configure the small detached antenna head only.
Dual-processor technology, real Lux-Off function for built-in application.
Zero-cross point operation, protect the sensor relay against the in-rush current, secure the max. load and lifetime of the relay.
DIP switch + IR Remote control 2 channels setting. Automatically override each other upon the latest operation.
RJ11 connection between the sensor body and antenna head, easy plug and play.
Detection range up to 12m in diameter.
Mounting height: 3~6m.
Operation temperature: -20 ℃~ +70 ℃
IP rating: IP20.
Settings(by DIP switch)--
Detection range can be reduced by selecting the combination on the DIP switches to fit precisely each application.
Hold-time means the time period to keep the lamp on 100% after motion detected.
*when hold-time set as 3s, sensor enters into test mode, this test mode is mainly for users to choose the desired detection range. In this mode, the daylight sensor is disabled, when there is no motion, fixture keeps off, when there is motion detected, fixture keeps a cycle of 3s on and 2s off.
Daylight sensor means the daylight threshold to enable or disable the sensor function.
"Disable”: The sensor works always, even during daylight.
"50lux, 25lux": The sensor works only in twilight.
"10lux, 2lux": The sensor works only in the dark.
Settings(by remote control IR12)--
Permanent ON/OFF function
Press “ON/OFF” button, fixture goes to permanent on or permanent off mode, sensor is disabled.
*press "Auto” ,”Reset" or “Ambient learn” to quit this mode.
Press “Auto” button, the sensor starts to work and all settings remain the same as the latest status before the light was switched on/off.
Press”Reset” button, all settings go back to the value of DIP switch settings.
Press "Ambient learn" button, the latest surrounding lux value overwrites previous lux value learned, and set as the daylight threshold. This feature enables the fixture to function well in any real application circumstance.
"Test mode"is for testing purpose only, for users to check the functionality and choose the desired detection range. The sensor goes to test mode automatically after pressing this button.
Users can quit this mode by pressing "ON/OFF", "Reset' or any button of "Hold time". The sensor settings are changed accordingly.
*Test mode defaulted settings—
In this mode, after motion detected, sensor enters into a cycle of 3s on and 2s off.
Utilizing the Dual-processor technology, this sensor can tell the difference of natural light and artificial light(lamp) from behind the diffuser, then switch off automatically whenever the artificial light is not required(ambient light is bright enough).
This is the REAL& INTELLIGENT lux-off sensor for built-in installation.
Note: Lux-Off sampling time--30s.