Microwave Motion Sensor Switch
Microwave Motion Sensor Module
Zhaga Book 18
Bluetooth Motion Sensor
Daylight Sensor Switch
12V Microwave Sensor
AC Motion Sensor Switch
High Bay Motion Sensor
Dimmable Motion Sensor
DALI Motion Sensor
Daylight Harvesting Sensor
High Frequency Motion Sensor
Presence Motion Detector
ETL Motion Sensor
Security Motion Sensor
LED Mirror Sensor
Advertising Display Sensor
Detached Version ETL Motion Sensor 1 ~ 10V Dimming Remote Settings
|Place of Origin||Shenzhen, China|
|Certification||RED, FCC, RoHS, ETL|
|Minimum Order Quantity||300pcs|
|Price||To be negotiated|
|Packaging Details||Bubble bag + carton. (color box or blister package also available on request)|
|Delivery Time||3~4 weeks for bulk orders|
|Supply Ability||30,000pcs / month|
Contact me for free samples and coupons.
Wechat: 0086 18588475571
If you have any concern, we provide 24-hour online help.x
|Input Voltage||120~277V AC 50/60Hz||Rated Load||400W@120VAC, 800W@200~277VAC (capacitive)|
|Control Type||1~10v Dimming||Stand-by Power||＜1W|
|Detection Range||Max. 12m In Diameter||Mounting Height||3~6m|
|Setting By||DIP Switches & Remote Control||Certification||ETL|
Detached Version ETL Motion Sensor,
Remote Settings ETL Motion Sensor,
Microwave Movement Sensor 10V Dimming
Detached Version , ETL Motion Sensor , 1 ~ 10V Dimming , Remote Settings
Sensor for American market, with tri-level dimming control(corridor function).
This sensor is particularly designed for light fittings where the inside space is very limited for a big normal sensor, for example the panels, the compact bulkheads, the linear office fittings. In such applications, only the detached small antenna head(ANT01/02) is needed on the outer surface, while the big sensor body and the drivers can be hidden behind the plate. Save space and reduce shadow that brought by the sensor body.
5.8GHz C-band microwave motion sensor, tri-level dimming control.
Input voltage: 120〜277V AC, 50/60Hz.
Rated load: 400W @ 120VAC (capacitive)
800W @ 200〜277VAC (capacitive)
Stand-by power: <1w.
Dual-processor technology, real Daylight monitoring function for built-in application.
Zero-cross point operation, protect the sensor relay against the in-rush current, secure the max. load and life time of the relay.
DIP switch + IR Remote control 2 channels setting. Automatically override each other upon the latest operation.
RJ11 connection between the sensor body and antenna head, easy plug and play.
Detection range up to 12m in diameter.
Mounting height: 3~6m.
Operation temperature: -20℃~ + 70℃
IP rating: IP20.
Settings(by DIP switch)--
Detection range can be reduced by selecting the combination
on the DIP switches to fit precisely each application.
Hold-time means the time period to keep the lamp on 100% after motion detected.
*when hold-time set as 3s, sensor enters into test mode, this test mode is mainly for users to choose the desired detection range. In this mode, the daylight sensor is disabled, when there is no motion, fixture keeps off, when there is motion detected, fixture keeps a cycle of 3s on and 2s off.
Daylight sensor means the daylight threshold to enable or disable the sensor function.
"Disable": The sensor works always, even during daylight.
"50lux": The sensor works only in twilight.
"10lux, 2lux": The sensor works only in the dark.
This is the time period that the lamp remains at a low light level before it is completely switched off in the long absence of people.
“+∞”: means bi-level dimming control, the fixture never switch off.
Stand-by dimming level
This is the dimmed low light level you would like to have after the hold-time in the absence of people.
*0% means on/off control.
10%--Vdim=1.5Vdc 30%--Vdim=3.0Vdc 50%--Vdim=5.0Vdc
Settings(by remote control IR12)--
Permanent ON/OFF function
Press “ON/OFF” button, fixture goes to permanent on or permanent off mode, sensor is disabled.
*press "Auto” ,”Reset" or “Ambient learn” to quit this mode.
Press "Dim" button to automatically dim up or down the light brightness during hold-time from 10% to 100%. Another press to lock it down when desired brightness is achieved.
*after desired brightness is locked down, if user wants to dim again reversely, just press the “Dim” button again and then lock down the new brightness again.
Press “Auto” button, the sensor starts to work and all settings remain the same as the latest status before the light was switched on/off.
Press”Reset” button, all settings go back to factory default settings.
*Factory default settings--
Press "Ambient learn" button, the latest surrounding lux value overwrites previous lux value learned, and set as the daylight threshold. This feature enables the fixture to function well in any real application circumstance.
"Test mode"is for testing purpose only, for users to check the functionality and choose the desired detection range. The sensor goes to test mode automatically after pressing this button.
Users can quit this mode by pressing "ON/OFF", "Reset' or any button of "Hold time". The sensor settings are changed accordingly.
*Test mode defaulted settings—
In this mode, when used for on/off control, after motion detected, sensor enters into a cycle of 3s on and 2s off. In this mode, when used for tri-level dimming control, after motion detected, sensor enters into a cycle of 3s on and 2s off(0.5s soft off + 1.5s off).
Daylight monitoring function--
Utilizing the Dual-processor technology, this sensor can tell the difference of natural light and artificial light(lamp) from behind the diffuser, switch on automatically(even without movements) when the ambient light is below target value, and then switch off automatically whenever the artificial light is not required(ambient light is bright enough).
This is the REAL & INTELLIGENT daylight monitoring sensor for built-in installation.
Note: Lux-Off sampling time---30s; Lux-On sampling time---10s.
Lux-On function takes effect only when standby dimming period set at+∞.