Sensor DIM Solution Microwave Motion Detector For Solar System Non - Dimmable Drivers
|Place of Origin||Shenzhen|
|Certification||RED, FCC, RoHS|
|Minimum Order Quantity||400pcs|
|Packaging Details||Bubble bag + carton. (color box or blister package also available on request)|
|Delivery Time||4 weeks for bulk orders|
|Supply Ability||40,000pcs / month|
|Input Voltage||8~30V DC||Rated Output||1.5A Max. (e.g. Max.18w@12v; Max.36w@24v)|
|Detection Range||Max. 12m In Diameter||Mounting Height||3~6m|
|Operation Temperature||-20℃ ~ +70℃||Dual Daylight Sensor||Yes|
|HF Frequency||5.8GHz||Product Guarantee||5 Years|
motion dimmer switch,
dimmer sensor switch
Sensor - DIM Solution , Dimmable Motion Sensor , For Solar System & Non - Dimmable Drivers
This sensor is specially designed for:
1 - solar system application.
2 - low voltage halogen lamp application.
3 - standard fixture with non-dimmable constant voltage driver.
Sensor-Dim function is easily achieved by just adding a single pcs HNS105!!!
5.8GHz C-band microwave, tri-level dimming function.
Input voltage 8~30V DC.
Rated output: 1.5A max. (e.g. max.18w@12v; max.36w@24v)
Dual-processor technology, real Daylight monitoring function for built-in application.
Detection range up to 12m in diameter.
Mounting height: 3~6m.
Operation temperature; -20℃ ~ + 70℃.
Hold-time means the time period to keep the lamp on 100% after motion detected.
*when hold-time set as 3s, sensor enters into test mode, this test mode is mainly for users to choose the desired detection range. In this mode, the daylight sensor is disabled, when there is no motion, fixture keeps off, when there is motion detected, fixture keeps a cycle of 3s on and 2s off.
Daylight sensor means the daylight threshold to enable or disable the sensor function.
"Disable": The sensor works always, even during daylight.
"50lux": The sensor works only in twilight.
"10lux, 2lux": The sensor works only in the dark.
This is the time period that the lamp remains at a low light level before it is completely switched off in the long absence of people.
“+∞”: means bi-level dimming control, the fixture never switch off.
Stand-by dimming level
This is the dimmed low light level you would like to have after the hold-time in the absence of people.