RoHS 12V Daylight Sensor Switch HNP102 8mA PWM 12V Microwave Motion Sensor
Contact me for free samples and coupons.
Wechat: 0086 18588475571
If you have any concern, we provide 24-hour online help.x
|Input Voltage||12/24V DC||Input Current||≥8mA|
|Output Signal||0~10V / PWM||Operation Temperature||-20 ℃ ~ + 70 ℃ .|
|Warranty||5 Years||Type||12V Microwave Motion Sensor|
RoHS 12V Daylight Sensor Switch,
Daylight Sensor Switch HNP102,
PWM 12V Microwave Motion Sensor
12V microwave motion sensor super compact with dual processor technology
Daylight Sensor with timer function and tri-level dimming for HNP102
DC input, tri-level dimming control and for real built-in daylight sensor
1. 12 / 24V DC input
2. Dual daylight sensor to distinguish natural light & artificial light
3. Really for built-in application
4. Tri-level dimming control
5. With timer embedded
6. 5 years warranty
|1.||Super compact, flexible to be integrated into any suitable fixtures.|
|2.||Dual-processor technology, distinguish natural light and artificial light(lamp) from behind the diffuser,
authentic daylight sensor for built-in application.
|3.||Tri-level dimming, not only for simple ON/OFF control, save more energy.|
|4.||Built-in timer, for end user to specify desired period to keep the light 100% on before dim down.|
|5.||8 pin DIP switch seting, multiple options to meet different customer demands.|
1. Daylight threshold
This is the threshold for the daylight sensor to switch on & off.
“Lux on”value means the daylight sensor will switch on when detected natural light is less than it.
“Lux off”value means the daylight sensor will switch off when detected natural light is more than it.
Note: Lux-on sampling time--10s; Lux-off sampling time--30s.
* when set as “Disable”, the daylight sensor will always be 100% on in both day and night.
2. Timer period
This is the period for the lamp to keep 100% on when natural light 5 is below set threshold.
*when set as “Disable”, this daylight sensor will become a simple on & off daylight sensor, switched
on 100% at insufficient natural light, switches off at enough natural light.
3. Dimming level
After the timer period, if the natural light is still insufficient, the lamp will drop to a pre-defined dimming
level. this dimmed level will sustain until the natural light becomes enough and the daylight sensor switch
*when set as 0%, means the daylight sensor will directly switch off right after the timer period elapses regardless
of the natural light, even in the mid-night.
Note--Defaulted factory setings as below:
Daylight threshold = 10lux
Timer period = 4h
Dimming level = 10%
Setings for below scenario: At 7:00AM, when natural light becomes sufficient, the daylight sensor
automati-cally switch the fixture off.