IP20 Microwave Motion Sensor Switch HNS203HB For High Bay Tri - Level Dimming Control
|Place of Origin||Shenzhen, China|
|Certification||RED, FCC, RoHS, ETL|
|Minimum Order Quantity||300pcs|
|Price||To be negotiated|
|Packaging Details||Bubble bag + carton. (color box or blister package also available on request)|
|Delivery Time||3~4 weeks for bulk orders|
|Supply Ability||30,000pcs / month|
|Input Voltage||120~277V AC 50/60Hz||Detection Range||Max. 18m In Diameter|
|Mounting Height||10~12m||IP Rating||IP20|
|Usage||High Bay||Product Name||Microwave Motion Sensor Switch|
microwave motion detector,
microwave sensor switch,
Microwave Motion Sensor Switch IP20
Microwave motion sensor switch ,High Bay Motion Sensor ,Enhanced Detection Range , Tri - Level Dimming Control
120~277V AC input,built-in use
Reinforced detection range up to 12~15m high, with daylight monitoring function.
specially designed for highbay fixtures(warehouse lamp / canopy / shoebox / gas station lamp / stadium lamp, etc).
1. Dual daylight sensor
2. Reinforced range for highbay
3. Tri-level dimming control
4. Daylight monitoring function
|1.||Input voltage:||120〜277V AC, 50/60Hz|
800W @ 200〜277VAC (capacitive)
|4.||Detection range:||Up to 18m in diameter|
|6.||Operation temperature:||-20℃~ +70℃|
8. 5.8GHz C-band microwave motion sensor, tri-level dimming control.
9.Dual-processor technology, real Daylight monitoring function for built-in application.
10. Zero-cross point operation, protect the sensor relay against the in-rush current, secure the max. load and life time of the relay.
11. RoHS compliant.
Daylight monitoring function:
Utilizing the Dual-processor technology, this sensor can tell the difference of natural light and artificial light(lamp) from behind the diffuser, switch on automatically(even without movements) when the ambient light is below target value, and then switch off automatically whenever the artificial light is not required(ambient light is bright enough).
This is the REAL & INTELLIGENT daylight monitoring sensor for built-in installation.
Note: Lux-Off sampling time---30s; Lux-On sampling time---10s.
Lux-On function takes effect only when standby dimming period set at+∞.