IR Remote Commissioning Dimmable Motion Sensor Switch CCT Dimming Control
|Place of Origin||Shenzhen, China|
|Certification||RED, FCC, RoHS, ETL|
|Minimum Order Quantity||300pcs|
|Price||To be negotiated|
|Packaging Details||Bubble bag + carton. (color box or blister package also available on request)|
|Delivery Time||3~4 weeks for bulk orders|
|Supply Ability||30,000pcs / month|
Contact me for free samples and coupons.
Wechat: 0086 18588475571
If you have any concern, we provide 24-hour online help.x
|Output||0-10v / PWM Signal||Channel||2 Channels|
|Product Name||Dimmable Motion Sensor||Detection Range||Up To 12m In Diameter|
|Mounting Height||3-6m||Functions||Tri-level Dimming & Tunable White|
motion sensor dimmer switch,
dimmer sensor switch,
CCT Dimming Dimmable Motion Sensor
12V/24V DC input dimmable motion sensor 2channels output integrated dimming control and tunable white functions super compact
1. Dual-processor technology, real Lux-off &daylight monitoring function for built-in application.
2. IR remote commissioning, easy setting and user friendly.
3. Easy access by DIP switch to shift between cool, white and warm.
|1.||Operating voltage:||12/24V DC|
|3.||Detection range||up to 12m in diameter|
|4.||Super compact||flexible to be integrated into any suitable fixtures|
|6.||Operation temperature:||-20℃ ~ +70℃|
|7.||Two channels output:||0~10V / PWM signal, achieve color temperature adjustments.|
8. Real Lux-Off function for built-in application.
9.Easy access by DIP switch to shift between cool, white and warm.
10. RoHS compliant.
Source current / Sink current: Max. 20mA; 0-10V leads can not be short-circuit.
Remote control Settings:
Press “” button, the motion sensor will be disabled.
press “” , “” or “” to re-activate the motion sensor.
Press “” button to automatically dim up or down the light brighness during hold-time from 10% to 100%. Another press to lock it down when
desired brightness is achieved.
Press “” button, the sensor starts to work and all settings remain the same as the latest status before the light was switched on / off.
Press “” button, all sensor settings go back to factory default settings.
Press “” button, the latest surrounding lux value overwrites previous lux value learned, and set as the daylight threshold. This feature enables the fixture to function well in any real application circumstance.
“Test mode”is for testing purpose only, for users to check the functionality and choose the desired detection range. The sensor goes to test mode automatically after pressing this button.
Users can quit this mode by pressing “ON/OFF”, “Reset”, or any button of “Hold time”. The sensor settings are changed accordingly .
Cool: Long press to adjust the color temperature towards Cool, release to stop and lock down current color temperature.
Warm: Long press to adjust the color temperature towards Warm, release to stop and lock down current color temperature.
Neutral: Press "Neutral" button, the color temperature will adjust to 50% cool + 50% warm.
CCT quick selection (DIP switch)
DIP switch + IR remote control 2 channels CCT setting. Automatically override each other upon the latest operation.