LED Light Switch HNS111HB 25mA High Bay Motion Sensor
|Place of Origin||Shenzhen, China|
|Certification||RED, FCC, RoHS|
|Minimum Order Quantity||300pcs|
|Price||To be negotiated|
|Packaging Details||Bubble bag + carton. (color box or blister package also available on request)|
|Delivery Time||3~4 weeks for bulk orders|
|Supply Ability||30,000pcs / month|
Contact me for free samples and coupons.
Wechat: 0086 18588475571
If you have any concern, we provide 24-hour online help.x
|Input Voltage||12V DC (24V Version Available On Request)||Input Current||≥25mA|
|Control Type||Infrared Remote Control IR12||Detection Range||Max. ∅18m|
|Mounting Height||10~12m For Warehouse||Operation Temperature||-20℃ ~ +70℃|
25mA Microwave Motion Sensor
High Bay Motion Sensor HNS111HB LED light switch for warehouse
You can use for warehouse lamp / canopy / shoebox / gas station lamp / stadium lamp, dual- processor daylight sensor for real built-in use, Reinforced detection range up to 12~15m high, infrared remote IR12 to change the parameters easily.
|Input voltage 12V DC (24V DC version available on request).|
|1~10V dimming signal|
|Detection range up to 18m in diameter.|
|Mounting height: 10~12m.|
5.8GHz C-band microwave, high bay version, and tri-level dimming control.
Dual-processor technology, real Lux -Off & Daylight monitoring function for built-in application.
IR remote commissioning IR12, easy setting and user friendly.
Settings(by remote control IR12)--
Permanent ON/OFF function
Press “ON/OFF” button, fixture goes to permanent on or permanent off mode, sensor is disabled.
*press "Auto” ,”Reset" or “Ambient learn” to quit this mode.
Press "Ambient learn" button, the latest surrounding lux value overwrites previous lux value learned, and set as the daylight threshold. This feature enables the fixture to function well in any real application circumstance.
"Test mode"is for testing purpose only, for users to check the functionality and choose the desired detection range. The sensor goes to test mode automatically after pressing this button.
Users can quit this mode by pressing "ON/OFF", "Reset' or any button of "Hold time". The sensor settings are changed accordingly.
*Test mode defaulted settings—